COMPARTMENTING AND FIRE PROOFING SEALINGS
PL 007 - PLASTERBOARD WALL
CROSSING OF THE COMBUSTIBLE PIPE
KM BOARD V1 mineral fiber panel, 150kg/m³ density with fire resistant coating on one side
KM-FS collar made up of a galvanized stell sheel, containing strips of graphitic intumescent material to seal pipes against the fire
KM SEALER F is a single component intumescent putty
Screw the four extension gussets and fit KM-FS on the PVC/PE/PPH pipe, shut the tongues and fix on the wall with through bolt.
Collar must be fitted on both sides of the wall.
Shape the panel KM BOARD V1 and seal the blank between pipe and wall; two panels must be fit up back to back with the treated side outwards. Seal with KM SEALER F putty
LAPI 4, pos 4.